Trusted Heating, Air Conditioning, and Plumbing Solutions for Vienna, VA Homeowners
Leave your indoor comfort and plumbing needs to our dedicated team. Call today to schedule your next heating, AC, or plumbing service in Vienna, VA.
You shouldn’t have to wait around wondering when your plumber or HVAC technician will show up. Get on-time service, personal attention, and an exceptional experience from start to finish when you call Service Specialties, Inc.–the local experts your neighbors in Vienna, VA turn to for top notch customer service and personalized solutions to meet your needs.
Top Notch Heating and Air Conditioning Services in Vienna, VA
Get professional answers to your HVAC problems and start enjoying total home comfort in no time when you choose Service Specialties. Our Vienna, VA heating and air conditioning service experts will work closely with you to understand your needs and comfort goals–so you can finally achieve total indoor comfort and energy efficiency for years to come.
Give us a call today to schedule a free consultation for HVAC replacements or to request immediate service for heating or air conditioning repairs in the Vienna, VA area.
Contact Our Vienna, VA Plumbing Company Today
We offer a variety of plumbing services and solutions to meet any need. Whether you need a minor repair or you are looking for a second opinion, our Vienna, VA plumbers are here to provide you with an honest recommendation and the quality results you deserve.
The last thing you want to deal with is a mess in your home due to a plumbing emergency. Leave all of your plumbing needs to our experts. We will take the time to identify the source of the problem, explain the best solution for your home, and present you with an upfront estimate before work begins–so you can easily make the best decision for your home. Our goal is to provide you with a stress-free experience from start to finish.
Contact us today to schedule a free estimate for installation or replacement, or to book an immediate appointment for heating, AC, or plumbing repairs in Vienna, VA.
for Vienna, VA
Checked system for wiring short in low voltage. I looked and replaced fuse and tripped again. I went looked through wiring and found common and O wires touching in air handler. Fixed wiring and now unit is functioning in cooling as it was before. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-3DD9-C7ABF87AD8C7409AAA4B02CB0BAD0E75
Conducted heating inspection on the three 80% gas furnaces and serviced both of the humidifiers on the main systems. All three HVAC systems are satisfactory and operating properly at this time. While on site, I also replaced two of the 413 media filters. One located on the primary basement system, and the other located at the attic unit. click the link below for additional information gathered during today’s heating inspections. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-3DD9-0A89F1F8040D42FEBA7B555A7DB44B5A
Autumn heating inspection performed on attic and basement gas furnace, no gas leak detected, checked voltage and amperage, cleaned flame sensors, temperature rise 35 degrees, media filters ok, inspected electrical connections, changed water on humidifier and tested for proper operation ok. Recommend adding two combustion air grilles on basement mechanical room walls, gas water heater is natural venting type. Informed homeowner that the more fresh air that the room gets the better for proper and safe combustion. Air Scrubber units are working at this time, View visual findings from this job here - https://visionshare.xoi.io/?id=XA-BE96-79C63D89EE23402A88DBCA93956C1A2A
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-BE96-56D9EF841F1C4C3589C2666CFC33B37E The thermostat confirmed operations at this time. The technician cleaned the cabinet and the electric box of the furnace all of the wires and electrical equipment are secure and satisfactory. The gas valve and the exhaust pipe are satisfactory. The igniter is severely worn the technician recommends replacing the igniter. The air filter is restricting the airflow 16 x 25 by one the technician replace the air filter customer supplied filter. The technician replaced the humidifier pad number 35 water panel and cycle dehumidifier the customer provided the water panel. The temperature rise were satisfactory across the heat exchanger. The heat exchanger has a tremendous amount of water damage there are pictures attached to the invoice along with a video. The technician recommends the customer start to maintenance the system otherwise they’re gonna have to replace it sooner than l
Upon arrival I met with customer and proceeded to install a new sump pump and a water powered backup. There is a one year labor warranty as well as the manufacturer’s warranty.