Your Preferred Manassas Heating, Air Conditioning, and Plumbing Company
Call now to schedule heating, air conditioning, or plumbing services in Manassas, VA or to request your free estimate and consultation for system replacements.
It shouldn’t be difficult to find qualified plumbing and HVAC professionals in your area. Service Specialties, Inc. is your local Manassas heating, AC, and plumbing company offering one-stop, full-service solutions to meet all of your needs. We service, repair, and replace all makes and models of heating and air conditioning systems, as well as handle a variety of plumbing jobs big and small. No matter your needs, our team will make sure you receive the top notch customer service and exceptional results you deserve.
Heating and Air Conditioning Services in Manassas, VA
We understand the heating and cooling needs of our neighbors in Manassas and will take the time to discuss your concerns and explain your options. Whether you are looking to proactively replace your air conditioner or heating system, or you need immediate help with equipment repairs, our team will have your HVAC needs resolved safely and efficiently.
Free consultations on HVAC replacements are available. Give us a call today to discuss your needs and learn more about your options for heating and AC repair or replacement in Manassas, VA.
Why Work With Our Manassas Plumbers?
Enjoy a more comfortable home environment and lower water bills with professional plumbing solutions that will give you the peace of mind you’ve been looking for. Our team is here to provide the fast solutions you need. Whether it’s a leaking faucet or a toilet leak, a water quality issue or a drain clog, you can count on our Manassas plumbing professionals to deliver the quality solutions you deserve.
Leave your HVAC and plumbing needs to the experts who are committed to ensuring your comfort and peace of mind. Call Service Specialties, Inc. today to schedule immediate heating, air conditioning, or plumbing services in Manassas, VA.
for Manassas, VA
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-A4F4-378D2712CB624D9CB20150091611F567
Waive Diagnostic Fee. The technician isolated the transformer the contactor the control board the thermostat and found a very very very small short on the contactor that would intermittently tripped the thermostat. The technician replace the contactor under warranty cycled the unit the system is operating properly at this time.
Arrived for an annual cooling maintenance inspection on a package unit system. Cycled system and verified temperature differential was satisfactory. Condensate line clear. Performed visual inspection of coils and blower wheel - fair. Readings across the system were within the manufacturers specifications. Checked the 16” flex duct and verified no sagging or water issues - good. System is cooling normally at this time. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-2C79-FB819FF4EC9547D9B02BB33688824FF1
The technician performed a courtesy inspection and cycled the unit the system is operating properly at this time. Final cycled unit three times systems operating properly at this time. The technician also help the customer navigation through the thermostat. the customer is now aware of how to dehumidifier and control the fan speeds for the different modes.
Work performed: no work performed; upon arrival client stated that they wanted to have their water heater flushed. And after further inspection found that the heater is at 8-9 years old and I recommended not flushing due to heater is on it’s tail end of life so therefore I left a recommendation for replacement due to age of heater.